This chapter presents assessment systems used around the world to measure green buildings, formulas for calculating Data Center energy efficiency, and an overview of industry organizations pursuing the development of each. This chapter also offers guidance for putting Data Center metrics in the appropriate context to understand a facility's performance.
By submitting your personal information, you agree that TechTarget and its partners may contact you regarding relevant content, products and special offers.
Why Measure in the Data Center
There's an often-used management adage that says you can't manage what you don't measure, and it certainly applies to Data Centers.
You not only need to accurately gauge your Data Center's capacity and resources to operate the facility effectively, but you also need to know how quickly you consume those resources and what type and quantity of byproducts the Data Center produces to know how green it is. Taking measurements is also crucial to determine the impact of any green improvements that you make upon the server environment. Without such information you can't know whether those upgrades have been successful, and if so to what extent, how fast their return on investment is, or how to prioritize future Data Center upgrades.
The reason to measure Data Center efficiency might seem obvious, but many companies apparently don't see value in doing so. Surveys of more than 1,500 Data Center owners and operators at DatacenterDynamics conferences in 2008 indicate that fewer than one in three were using a Data Center efficiency metric and fewer than half definitely intended to use them in the future.
Just 461 (30.3 percent) of 1,523 respondents indicated they use a Data Center efficiency metric, according to the Datacenter Research Group that performed the studies, whereas the remaining 1,062 (69.7 percent) reported they did not. When the same group was asked whether they plan to employ efficiency metrics in the future, 642 (42.2 percent) indicated they did whereas 492 (32.3 percent) indicated they did not. The remaining 389 (25.5 percent) did not reply or else indicated that they did not know.
Table 2.1 summarizes the results, broken down by geographic theater. Interestingly, those in the United States appear to be using Data Center metrics most often yet those in Western Europe have the greatest intention to do so in the future.
It's possible that the survey results in Table 2.1 show a greater adoption of Data Center metrics than is truly happening. All the survey participants were, as noted, attendees at Data Center conferences. Companies that commit money and staff time for employees to attend such events are actively seeking Data Center best practices for their facilities. How many more businesses, particularly those with makeshift server environments, aren't sending employees to such conferences and aren't focusing on the efficiency of their facility?
What to Measure in the Data Center
Knowing the importance of taking measurements in your Data Center, what elements are useful to measure to evaluate how green a room is and to quantify the impact of various upgrades? The sections that follow address this question.
The single-most important resource for you to measure in your Data Center is energy. How much power the facility has and how much power is consumed by both IT equipment and supporting infrastructure such as cooling systems and lighting.
It's vital to measure energy for several reasons:
- Power is a Data Center's most precious resource: The small form factor and big energy demands of today's high performance servers mean most Data Centers will run out of power well before cabinet space or cooling. Even if you aren't interested in green considerations, measuring energy usage is critical to understand the true capacity of the room.
- Power is the common element among disparate Data Center subsystems: Air handlers, servers, and overhead lighting are all different infrastructure of a Data Center -- so different that they're each installed and maintained by personnel that are trained in separate disciplines -- yet they all need power to function. Measuring energy consumption creates a common standard by which you can tell how much they're each drawing upon your overall Data Center capacity.
- Power consumption is the most expensive operational cost of a Data Center: By measuring the specific energy usage of various Data Center components and applying the regional cost of electricity, you learn the true monthly expense of those components. This enables you to target which Data Center subsystems have the potential to save you the most energy and the most money through efficiency improvements.
- Power consumption largely defines a Data Center's environmental impact: The amount of power that a Data Center uses on a day-to-day basis determines how much irreplaceable fossil fuels it consumes and the quantity of carbon emissions it is responsible for.
Because of these four conditions, green Data Center improvements that conserve energy provide some of the largest benefits to your business. Measuring power in your Data Center is, therefore, also the best way to appraise that value and understand the real impact of those green improvements.
Another benchmark of a Data Center's environmental impact is its carbon footprint -- the amount of carbon dioxide produced as part of the ongoing operation of the facility.
Carbon dioxide is one of a handful of substances dubbed greenhouse gases that trap heat from the sun and warm the Earth. (Water vapor is the most common greenhouse gas, followed by carbon dioxide, methane, nitrous oxide, ozone, and chlorofluorocarbons.)
That warming effect is necessary to a certain degree. Without it, the Earth's mean surface temperature would be --2 degrees Fahrenheit (--19 degrees Celsius) rather than today's 57 degrees Fahrenheit (14 degrees Celsius), according to the Intergovernmental Panel on Climate Change document, "Climate Change 2007: The Physical Science Basis." Too much warming can cause environmental problems, though, changing weather patterns, causing sea levels to rise, and altering the habitats of various animals, plants, and, ultimately, people.
Many scientists and environmentalists today are concerned that human activity is causing such problems, prompting them and various government agencies worldwide to call for reductions in carbon dioxide emissions. Although carbon dioxide occurs naturally -- people, animals, and plants all produce it; volcanoes and hot springs emit it as well -- carbon is also a byproduct of burning fossil fuels.
More than 80 percent of greenhouse gas emissions in the United States, for example, are energy-related carbon dioxide -- originating from the combustion of petroleum, coal, and natural gas -- according to the U.S. Department of Energy's Energy Information Administration. (EIA reports of U.S. greenhouse gas emissions are available online for every year since 1996 at http://www.eia.doe.gov/oiaf/1605/ggrpt/index.html.)
The links from energy production to carbon dioxide to climate change mean that the less energy your Data Center uses, the smaller its impact upon the environment.
The other factor in a server environment's carbon footprint is the makeup of the electricity powering the facility. Several sources of energy are used to create electricity, and each generates a different amount of carbon dioxide. Turning coal into electricity produces more carbon dioxide than natural gas, for instance, so your Data Center will have a larger carbon footprint if your regional power company provides electricity derived from coal rather than natural gas. Cleaner energy sources, such as nuclear or hydroelectric power, create minimal amounts of carbon dioxide, so any Data Center powered by those sources, either directly or by way of a utility provider, will have an even smaller carbon footprint.
One strategy for dealing with carbon emissions is to employ carbon offsets, measures that reduce carbon dioxide. In simple terms, you compensate for the amount of carbon that you (or in this case, your Data Center) generate by sponsoring a project that prevents an equal amount from being created.
Examples of carbon offsets include
- Providing a source of renewable energy, such as biofuels, hydroelectric, solar, or wind power
- Planting trees, which serve as natural carbon sinks
- Capturing and eliminating more potent greenhouse gases, such as methane produced by landfills or pollutants (that is, hydrofluorocarbons or perfluorocarbons) created during industrial processes
Although it's possible to directly introduce carbon-offsetting measures at your Data Center facility -- building a wind farm on land that you own, for example -- the more common approach is to pay an environmental organization to do the activity.
More information about renewable energy sources and regional electricity mixes is provided in Chapter 4, "Powering Your Way to a Greener Data Center."
Other Data Center Elements
Energy usage and carbon footprint are the features most commonly discussed and measured to determine how green a Data Center is; however, other elements warrant attention as well. Other green details to consider include the following:
Generator emissions: Standby generators, used to keep a Data Center running when commercial power fails, consume fuel when in operation and can emit a range of pollutants including nitrogen oxides, hydrocarbons, carbon monoxide, carbon dioxide, and particulate matter. Knowing the consumption and emissions of your Data Center generators provide greater insight into the facility's environmental impact.
Heat waste: Most strategies regarding Data Center temperatures focus on how to best remove hot server exhaust from the hosting environment yet pay little attention to the ultimate disposition of Data Center heat waste. If your Data Center cooling system is highly efficient and does a superb job of keeping equipment cool but raises temperatures outdoors, how green is it really? Hot building exhaust is blamed for increasing the severity of several undesirable environmental and health problems including air pollution, heat-related illnesses, deteriorated water quality, and increased energy consumption during summer evenings. The phenomenon known as heat islands is discussed further in Chapter 3, "Green Design and Build Strategies."
Water consumption: Major Data Centers consume millions of gallons/liters of water per month through standard cooling processes as hot water is vaporized from a Data Center's cooling tower and has to be replaced. (Water used to replace what has evaporated is known as makeup water.) Although this consumption hasn't received the same level of attention from governments and the public in recent years as energy use and carbon emissions, removing such large amounts of water from local supplies is a tremendous environmental impact.
The more of these Data Center elements that you measure, the more opportunities to make your server environment greener that you uncover. Tips on reducing the impact of these features are provided in Chapter 4 and Chapter 5, "Cooling Your Way to a Greener Data Center."
Printed with permission from Cisco Press. Copyright 2009. Grow a Greener Data Center: A guide to building and operating energy-efficient, ecologically sensitive server environments by Douglas Alger. For more information about this title and other similar books, please visit Cisco Press.